I spoke to Broag today about one that's had 2 transformers, electodes and burner seal for an E5. Steady 8.8% co2 but I could see the ionisation current dropping to as low as 1.9. They said to watch the 02 level if that was around 5.5% replace the ignition transformer again.
- Posts : 17
Join date : 2009-11-19
If its on a vertical flue, check co2 with case on. I have had 2 now that was ok with case off, but when the case went back on the co2 went of the scale and locked up my fga. Spoke to broag, it is caused by the inner flue seals split or pushed out, also noticed signs of condense running into boiler from vertical flue. Passed back to installer.
- Posts : 1
Join date : 2010-02-11
Permissions in this forum:You cannot reply to topics in this forum