When changing the fan assy on these boilers it's advisable to replace the foam seals as this can cause air to be drawn in around the seals and effect the air/gas mixture resulting in the boiler failing to ignite. Also check for a green label on the combustion chamber saying burner ok as Buderus have also introduced a burner modification.
- Posts : 17
Join date : 2009-11-19
Permissions in this forum:You cannot reply to topics in this forum